SEITRON GAST signaling device
Burning gas with very dangerous and toxic does not have a smell and color, a person cannot determine or feel, but inhaling him in a small concentration can lead to death. New technological studies have allowed the development of the Seitron gasket, a device that determines the accumulations that are dangerous for human life. Seitron the aggregation signaling device is intended for timely detection from carbon monoxide on parking lots, in boiler rooms and residential premises. Two thresholds of the operation and 2 output relays on each threshold, the sound and light alarm system is equipped, the discharge button. 230 in power voltage and IP40 degree of protection. The Seitron gasket alarm is equipped with sensitive devices that provide preliminary anxiety and the main. The trigger depends on the concentration of CO in the room.
Pre -alarm alarm, the device is triggered if the concentration of carbon monoxide already exceeds the limit of 20 mgm3. The red -red LED begins to blink and begins to work the first threshold of relay 1. Anxiety The main or 2 sensitive threshold of the device works when the concentration of 100 mgm3 exceeds. The warning indicator glow continuously red and begins to sound an alarm beep and relay 2 is triggered. The sound of the signal and the relay work until the “reset” button located on the instrument panel. Even if the concentration of carbon monoxide and decreases below the alarming threshold. It is possible to connect an additional protective and signaling equipment to the detector mounted in the detector.
The usual operation of the carnered gas control detector in the room occurs after 15 seconds, since the device is equipped with an automatic diagnostic system. There is a yellow flashing indicator on the front panel, notifies the malfunction of the sensitivity element. Green indicator – about the readiness of the device to work for air analysis. Check the operation of the relay, sound alarm and indication devices are made for 5 seconds by pressing the control button located on the facade panel of the device. The detector with is equipped and a delaying device that prevents the operation of an alarming system. After turning on the device, the process of self -control passes and the relay is blocked.